It is very important that the air compressor should run in good working condition to deliver the best result, for this, we have to take care of this important engineering utility. we cannot keep one operator for a full time near to compressor & keep watching the performance. That is why it is necessary to provide some safety switches in control panel. These safety devices will work in abnormal condition & stop electric motor and further prevent any breakdown in Air Compressor.
Many safety switches are used to avoid any accident to an air compressor. Out of that, the most important safety switch is “Low oil pressure switch” in short LOPS as the name indicates; this switch will operate in condition when the oil pressure in the crankcase is lower than set limit & stops the compressor.
The details of LOPS is as below INDFOS make IPS-70 switch is commonly used & the function of this switch is to monitor the oil pressure in the crankcase of an air compressor. This switch is connected to the oil pressure sensing line coming from the crankcase to the oil pressure gauge, through Tee connection.
The main spring can be set to balance different pressure on the bellows. When the pressure increases, the bellow is affected so that the main spindle is moved upwards until the spring pressure balance the bellow pressure. The spindle has guiding knob and differential adjusting nut which jointly transmit the spindle movement to the switch.
The differential pressure has to be set at zero (Indicator scale at extreme left, facing to LOPS) and the main scale is set to required pressure. (Minimum oil pressure required by the compressor. i.e. 14 PSIG for reciprocating air compressor & 35 PSIG for rotary air compressor).The pressure on the main scale can be set by rotating the knob given at top of the switch.
How to set & test Low Oil Pressure Switch (LOPS).
Connect an Ohmmeter across normal open contact of the switch to observe the switch operation. Start the compressor and watch the oil pressure at which contacts closes, then stop the compressor to see at what oil pressure contacts opens. By adjusting the knob further fine adjustment can be done to the exact pressure required. So confirm the setting by starting & stopping the compressor. Since the switch remains open during starting, a normal close contact of the timer is connected across the normal open contact of LOPS. The timer is set for 60 sec. As the compressor starts, timer starts its timing cycle and the compressor oil pressure also start building up in 60 sec. timer contacts will becomes open. Due to developed oil pressure in sensing line, LOPS contacts closes & continued the healthy running condition of air compressor.
Some other useful articles…